It looks like you're using an Ad Blocker.
Please white-list or disable AboveTopSecret.com in your ad-blocking tool.
Some features of ATS will be disabled while you continue to use an ad-blocker.
"The technology we have today is nearly a hundred years old," says Eric Kozubal, a senior engineer at NREL. Kozubal and colleagues have come up with an air conditioner that combines evaporative cooling with a water-absorbing material to provide cool, dry air while using up to 90 percent less energy. The desiccant-enhanced evaporative, or DEVap, air conditioner is meant to addresses the old complaint, "It's not the heat; it's the humidity," more efficiently.
Evaporative cooling--blowing air across a wet surface to promote evaporation--has long been used in so-called swamp coolers. A method called indirect evaporative cooling improves on this design, dividing air into two streams, which separated by a polymer membrane. Water is passed through one airstream, making it cooler and wetter; the cool air cools the membrane, which in turn cools the air on the other side without adding water.
But air can only hold so much water vapor, so in humid climates the effect is limited. On a 32 ºC day in Houston, Kozubal says, evaporative cooling may only bring the temperature down to about 27 ºC. Ideally, to provide a comfortable building, an air conditioner should cool air to 13 or 16 ºC.
NREL overcomes the humidity problem by adding another step, the use of a material known as a desiccant that absorbs moisture. NREL uses a liquid desiccant, a syrupy solution of lithium chloride or calcium chloride, about 44 percent salt by volume. In this setup, another membrane separates the desiccant from air traveling through a channel. The polymer membrane has pores about 1 micrometer to 3 micrometers in diameter, big enough that water vapor passes through easily while the salty liquid stays put. The membrane is also coated with a Teflon-like substance to repel liquid water. The desiccant pulls moisture from the airstream, leaving dry, warm air. Then it's back to indirect evaporative cooling: in a second channel, water evaporates to cool a secondary airstream, which in turn cools the first airstream, and out comes cool, dry air.
Some commonly used desiccants are: silica gel, activated charcoal, calcium sulfate, calcium chloride, montmorillonite clay, and molecular sieves.
- more details for each one at the link.
Become a fan of fans, Cut back the transfer of heat through the roof and walls. Weatherize your home to reduce the loss of conditioned air, Install a foil radiant barrier in the attic. Let hot air out of your attic ,Install inexpensive heat-reflecting film on windows that face the sun, Install skylights.,Reduce heat gain by pulling drapes or shades, Turn on the sprinklers., Plant now to provide shade in the future, Closely monitor the temperature both inside and out, Reduce indoor humidity, which makes room air feel warmer, Turn off heat-generating lights and appliances
Originally posted by Maxatoria
reply to post by Wrabbit2000
looking at that picture you need a deep enough hole and a fan to pull the air through the cooler ground